How to use a Sanitary pressure reducing valve?
Step 1. Close the gate valve in front of the pressure reducing valve and open the gate valve after the pressure reducing valve to create a downstream low-pressure environment;
Step 2.Adjust the screw.Turn counterclockwise to the uppermost position (relative to the lowest outlet pressure), and then close the gate valve of the pressure reducing valve;
Step3. Littlely pen the beforehead gate valve to fully on;
Step 4. Turn the adjusting screw slowly clockwise to adjust the outlet pressure to the required pressure (based on the gauge behind the valve); and then lock it tightly.then open the gate valve after the pressure reducing valve;
Step 5. If the outlet pressure is higher than the set pressure during adjustment, you should re-adjust from the beginning
Sanitary pressure reducing valves are mostly used in food, pharmaceutical, dairy, clean room, biological engineering and other high clean areas.
|Size||DN15 ~ DN80(1/2 "~ 3")|
|Connection ends:||Butt welded.tri clamped,threaded,flanged|
|Inlet Max Pressure:||145PSI/10BAR|
|Outlet pressure Range:||0.8 ~ 8Bar|
|Max temp||165 °C|